This is a potential security issue, you are being redirected to http://nvd.nist.gov
Last updated: 4/28/2016 9:34:23 PM
CVE Publication rate: 19.7
NVD provides four mailing lists to the public. For information and subscription instructions please visit
NVD Mailing Lists
Stack-based buffer overflow in the ODBC server service in Citect CitectSCADA 6 and 7, and CitectFacilities 7, allows remote attackers to execute arbitrary code via a long string in the second application packet in a TCP session on port 20222.
The vulnerability found in CitectSCADA could allow a remote un-authenticated attacker to force an abnormal termination of the vulnerable software (Denial of Service) or to execute arbitrary code on vulnerable systems to gain complete control of the software. The CitectSCADA and CitectFacilities applications include ODBC server capabilities to provide remote SQL access to a relational database. For that purpose, an ODBC Server component is used to service requests from clients on TCP/IP networks. Requests are serviced over a TCP high-port in which the application layer protocol reads an initial packet that specifies the length of data and then a second packet of data, of the same length is then read. Once the data is read from the network, it is then copied to an internal buffer of fixed size allocated in the stack without previously verifying that the buffer is big enough to store all the read data.
The vulnerability is related to a lack of a proper length-checking on data read from the network. A specially crafted combination of length and data packets could be used to exploit the vulnerability allowing an un-authenticated attacker to execute arbitrary code on vulnerable systems.
The bug is a texbook example of classic simple stack-based buffer overflow vulnerabilities of the 1990s that can be exploited by overwriting the return address of the currently running thread.
Fixes and Workarounds:
User organizations should deploy the vendor patch, which is available upon request at http://www.citect.com/ or disable the vulnerable service (ODBC server) if it is not needed in their particular installation.
Citect will provide a patch upon request to mitigate this vulnerability. Please see the following press release for more information:
For further information on properly securing SCADA systems, please see the following whitepaper published by Citect:
By selecting these links, you will be leaving NIST webspace. We have provided these links to other web sites because
they may have information that would be of interest to you. No inferences should be drawn on account of other sites
being referenced, or not, from this page. There may be other web sites that are more appropriate for your purpose.
NIST does not necessarily endorse the views expressed, or concur with the facts presented on these sites. Further,
NIST does not endorse any commercial products that may be mentioned on these sites. Please address comments about
this page to email@example.com.
& Privacy Statement / Security Notice
Send comments or suggestions to firstname.lastname@example.org
NIST is an Agency of the U.S. Department of Commerce
NVD Services Version 3.5
Full vulnerability listing